so i walk down to the DB to take a look at the circuit breaker and do some tests...and what do i find...
just what i expected...and people wonder why i am so sick and tired of being an electrician...can not one person just do their %^&*$ job right.
can anyone see anything wrong with this DB?
no circuit labels
no in case of...label
when i opened it i found a transfomer for the elctric fence inside the DB with the 1.00 mm cabtyre connected directly to the bottom of the e/l unit.
a 0.25 mm piece of cabtyre connected to the light circuit 15 amps breaker.
the keypad mounted on the db cover so when you take off the front panel it hangs on 2 small little signal wires...is this even legal?
connecting an electric fence to an e/l unit must be half the problem...especially when it rains and the fence shorts out...surely you dont connect an electric fence to an e/l unit?