I need to issue a COC but refuse because the factory is not up to scratch.I have been at it for 3 months now and still not finished.(I am permanently employed by them)The fact that my job is on the line does not bother me.I try to be honest all the time and this factory will not pass in any way. The bosses son has brought in a "tame" sparky who will issue a COC for the factory as it stands.Can I post some pics and details and you guys tear it apart and tell me who is wrong?
Some examples as a teaser:
1)50 mm 4 core rubber trailing cable 70mts long used as a permanent supply to a test bench with a step up transformer with no safety equipment and only a 400 amp breaker to switch the transformer.Connected to the municipal supply with no meter etc.
2)Plugs and lights connected to a 125 amp isolator direct(no switching etc)
3)DB's and isolators bricked closed.(I am still trying to find all of them)